Harmonic Filter Reactors
De-tuning reactors re used to tune the capacitor bank to desirable frequency in order to avoid the probability of Harmonic amplification and thereby protect the capacitors from adverse effects of harmonics. They also help in limiting switching inrush current.
Viz reactors are designed for low loss, 3 phase assembly complete with mounting brackets and connecting cables.
Viz offers wide range of reactors from 230V to 1000V systems for capacitors banks rated from 5 KVAR to 1000 KVAR with impedances of 5.67%, 6%, 7% and 14%(of capacitor bank).
|Specifications of Detuned Reactor|
|KVAR Rating||5 to 100KVAR|
|No of Phase||3Ph|
|Core used||Iron Core|
|Conductor used||Copper or Aluminium|
|Linearity||up to 180%|
|Insulation Temperature Class||H|
|Ambient Temp.||50° C Max|
|Type of Termination||Copper terminal|
|Insulation Level||3KV For 1 Minute|
|DC Insulation Resistance||200MΩ Measured with 500V DC Megger|
|Noise Level||Noise Level|
|Detuning Factor||7% & 14%|
|Nominal Voltage||400, 415 & 440V|